for decentralized hot water
The domestic hot water station BM-T is used as a home station for the multi-storey and single-family homes.
Decentralized hot water production:
The domestic hot water is heated only during the request through a stainless steel plate heat exchanger in the flow principle. In heating systems with buffer, the heating water, according to the pressure loss during the dispensing process,
by means of a central controlled circulating pump pumped through the heat exchanger.
The station can be connected directly to a secondary district heating network or CHP system.
Proportional controler PM-TD with thermostatic adjustment and internal differential pressure control, for quantity and temperature-dependent control of DHW heating.
The proportional controler ensures a constant DHW temperature regardless of the quantity taken, the heating water temperature or the tap intervals.
A universal mounting distance 80 mm for surface water meter and a universal mounting distance 110 mm for heat meters to 1.5 Qn are integrated in the distribution cabinet.
|Cabinet size:||410 x||800 x||110-150||mm|
|Pressure rating:||PN 10||PN 10||PN 10||PN 10|
|Heating water flow temperature:||max. 90 °C||max. 90 °C||max. 90 °C||max. 90 °C|
|Setpoint temperature hot water:||45-65 °C||45-65 °C||45-65 °C||45-65 °C|
|Pressure cold water:||2,0 bar||2,0 bar||2,0 bar||2,0 bar|
|Example performance heat exchanger|
|DHW performance:||29 kW||36 kW||45 kW||51 kW|
|Flow / return temperature primary:||60/25 °C||60/25 °C||60/25 °C||60/25 °C|
|KW entry / DHW outlet temperature:||10/50 °C
|DHW tap load max.:||10,5 l/min
|Min. Required differential pressure:||350 mbar||350 mbar||350 mbar||350 mbar|
|Flow Primary:||705 l/h||875 l/h||1095 l/h||1240 l/h|